Root Cause Failure Analysis of a Circulating Water Pump Impeller
A pump in the circulating water system of a nuclear plant experienced excessive vibration. The pump was removed from service and inspection showed that one of the six impeller vanes had failed.
The root cause of a circulating water pump impeller failure was attributed to the change in the discharge expansion joint installation practice. This change allowed up to 1-inch of expansion and 1-1/2-inch of compression clearance in the 6 axial expansion joint control rods.
This change altered the fluid force transmitted to the pump discharge flange affecting the impeller to shroud running clearance. Additionally, the replaced joint had a different stiffness that altered the dynamic response of the pump. KEI provided recommendations to restore the previous pump discharge expansion joint control rod configuration.
Contact us today to know more about the root cause failure analysis of a circulating water pump impeller and how we can help.